21-day Money Back Guarantee
Power Capacitors Limited (PCL) offers a 21 day no obligation money back guarantee (carriage excluded) on condition that the converter is returned to PCL in a state fit for resale. No handling charge will be raised.
The TRANSWAVE converter is covered by a 2-year parts warranty against failure due to faulty manufacture, further details of which are available on request. Extended warranties are also available on request.
CE marking/EMC Compliance
Power Capacitors Limited manufactures and sells CE marked products compliant with EMC regulations, The Low Voltage Directive and BS EN ISO 61000-3-2:2006. The company can provide, on request, a Declaration of Conformity (DOC) for every product.
ISO9001/2015 - Quality Assurance
We believe that the TRANSWAVE Converter is the only converter manufactured in an ISO9001/2015 quality assured manufacturing facility. PCL was first accredited with a British Standard in 1996. Over 25000 units have been sold to OEM’s, machinery dealers and end-users since 1984. The Company employs 20 people in the UK and achieved an annual turnover in excess of £2.7 million in the financial year 2019.
Sales engineers are available on our Direct Dial Helpline (0121 708 4522 or FREEPHONE 0800 0352027) from Monday to Friday 8am to 5pm to answer any sales or technical support issues. Answering machine service available otherwise.
Most compressor motors can be operated successfully using static converters. Direct-on-line starting is essential. A rotary converter is recommended for Hydrovane-style systems. In all instances please ensure that you advise the motor size and current rating before ordering.
Aluminium Bodied Motors
Aluminium motors may not operate successfully in conjunction with static converters. We would recommend the use of a rotary converter to address this issue where necessary.
Brake Testing Equipment (MOT)
The use of a rotary converter is recommended for both Class 4 and Class 7 brake testers.
These applications are regularly used in conjunction with static converters. Ensure that you advise the motor size, current rating and style of car ramp (electro-mechanical or hydraulic) at the point of enquiry. Hydraulic ramps generally work a motor to full load whereas screw-type electro-mechanical ramps often work a motor to short term overload. Plated motor currents often suggest a higher short-term kW demand - e.g. a 3kW/8A motor would suggest the motor is likely to develop 4kW so we would recommend a 5.5kW converter rather than the 4kW unit. (Note that a 3kW motor on a machine tool would only be plated at 6.5A). The power regulator switch fitted to the converter may have to be adjusted in line with a variation in load. Even though the ramp may have a 3 ton capacity mechanically, the artificial nature of the supply created by a converter may result in one power setting to lift a Ford Mondeo and another to lift a Land Rover. The operation of the equipment in conjunction with a converter may involve some operator discipline. The rotary converter may offer a more operator-friendly solution.
Collection or Delivery
You are welcome to collect your converter from our Birmingham factory. Delivery charges reflect the use of third party parcel and pallet carriers. Remember that both rotary converters and larger static converters are particularly heavy and will arrive either on a pallet or in a crate via a tail-gated delivery vehicle. You may wish to have more than one person available to accept delivery. Please endorse any palletised delivery “unchecked” when signing for the consignment.
Continuous Duty Applications
We do not recommend the use of TRANSWAVE Converters for applications which operate on a 24hr/day continuous duty. Where a converter is used 24/7 the warranty will be reduced to 12 months. For remote, non-operator controlled, cyclic-duty applications such as refrigeration compressors and pumps, the need for an “on-demand” supply is often accommodated by static converter. See “refrigeration compressors and pumps” below.
D.C. braking circuits (rectifier circuits) and lighting circuits (control transformers).
There is more room for error connecting these circuits to a converter output than would be experienced on a mains three-phase supply. Two specific phases must be connected to 415v 2-wire circuits, both on rotary and static converters. Similarly a specific phase has to be selected for 240v phase-neutral requirements. In some instances, particularly woodworking applications, a wiring diagram of the braking circuit would be helpful as it may be necessary to modify the control wiring of the machine to ensure that the braking circuit is connected to the same two phases as the starter control circuit. This ensures the successful operation of the brake/light. Failure to identify the need to modify the circuit or connecting to the wrong phases could lead to malfunction of the braking mechanism or light.
Digital Phase Converters/Modified Inverters
A standard converter varies voltage from 240/415 but fixes the supply frequency at 50Hz. A standard inverter fixes voltage at 240/240 but varies the supply frequency. Any digital inverter device that varies voltage from 240/415 has been modified away from its original design specification. Please seek advice before considering this type of device as it is unlikely to comply with regulatory requirements governing the use of inverters.
Frequency Converters/Inverters and Variable-Speed Drives (VSD/VFD)PCL is a Tier One Reseller of IMO Inverter Products. All inverters are offered with a 2-year manufacturer’s warranty. Please ask for details.
See “Resistive Loads”
Hi-Torque Starting Requirements
Standard specification static and rotary converters operate the vast majority of applications successfully. However there are instances where additional starting performance is required for applications such as screw-type car ramps where the plated motor current suggests a higher short-term kW demand than stated on the motor plate. Similarly some machine tools offer mechanical ratios in excess of the synchronous speed of the motor. A standard specification static or rotary converter will invariably only start a 1:1 ratio of motor to geared speed, particularly where there is a direct-drive rather than a clutch-assisted start. For example: the Harrison M300 lathe is driven by a 3hp 1400rpm motor but has a top mechanical speed of 2500rpm. The standard specification converter is likely to achieve only 10 of its 12 mechanical speeds; however the hi-torque version should achieve all 12. Please do not hesitate to seek further advice from the company’s sales engineers if you are unsure as to which size of converter is suitable for your application.
Inverters/Frequency Converters and Variable-Speed Drives (VSD/VFD)
PCL is a Tier One Reseller of IMO
Inverter Products. All inverters are offered with a 2-year
manufacturer’s warranty. Please ask for details.
Motors & Motor Control Packages
PCL is a stockist of TEC motors in both Metric and B56 Imperial Frame Sizes. Motor Control Packages are available for both single and three phase supplies. Please ask for details..
Variable Demand Environments - Multi-Motor and multi-operator applicationsThe rotary converter is the most appropriate solution for these examples as it automatically adjusts in line with any variation in demand or sequence of motor starting. If considering the use of a static converter, sequential starting (large followed by small) is necessary and the power regulator switch will have to be adjusted in line with any variation of demand. This is likely to prove impractical.
Multi-speed or Pole-change motors. Applications requiring frequent stopping and starting.
It may be prudent to consider the use of a rotary converter for these applications. Otherwise a pilot motor may be required with a static converter if the magnetic characteristics of the motor do not lend themselves to the creation of a satisfactory artificial phase. Motors with 720rpm and 960rpm windings may prove problematic. Please do not hesitate to seek further advice from the company’s sales engineers.
All standard static and rotary converters are fitted with a 5-pin 3-phase neutral and earth socket offering the facility for both 415-volt and 240-volt control requirements. A 16A or 32A plug is supplied free of charge with the converter as a loose item. Rotary converters from 15kW and upwards are fitted with output terminals for “hard wiring”.
Machines without an inching facility can be operated directly from a suitably rated static converter. Applications requiring an inching facility must be operated in conjunction with a rotary converter to avoid electrical damage to the motor windings. Japanese printing machines (e.g. Ryobi) often incorporate 200 volt three phase motors, connected to a mains supply via a three-phase 200/415-volt transformer. To ensure successful operation of the machine, the use of a rotary converter is recommended, together with a means of isolation between the converter output and the three-phase transformer.
Produce Conveyors, Grading and Potting Equipment.
Care should be taken to ensure that the TRANSWAVE converter rating is high enough to enable the motor to start under a load condition. Be wary of multi-motor applications where it may be necessary to consider a rotary converter or to ensure that one motor is running constantly to allow fractional horsepower ancillary motors to switch on and off at will. Other solutions to minimise this impracticality are available using individual capacitor circuits. Motors sized below the minimum loading of the converter will be damaged if operated independently from any converter other than the rotary. Please seek further advice from the company’s sales engineers if unsure as to which converter to order.
Pump applications (slurry/dirty water - irrigation/clean water), aerators and mixers
Most installations of this nature are controlled remotely, rather than via an operator. The majority of converters manufactured for this type of application are of the “Hi-Torque” static style, often custom-built. The recommended converter rating is determined by the duty cycle of the motor - i.e. cyclic or continuous - the application, motor current, power rating and speed. On-site commissioning by a PCL engineer or qualified electrician is recommended; technical assistance is available if required.
Compressor motors can be operated successfully using the “Hi-Torque” static converter. For motor sizes in excess of 2.2kW/3hp the fitting of an off-load valve is advisable. Direct-on-line starting is essential. The use of a rotary converter is recommended for Hydrovane-style air compressors. In all instances please ensure that you advise the motor size and current rating before ordering.
Resistive Load (Heating Elements)
Phase Converters are not designed to support resistive load such as Heating Elements, Ovens, Chip Fryers, Pizza Ovens, and Sunbeds. We are not aware of any product capable of supporting this type of three-phase load on a single phase supply. Such demands often take the form of three separate single phase elements with a common neutral.
Shock-Load applications (e.g. Sheet Metal Equipment such as Guillotines & Presses)
The use of a rotary converter is recommended for these applications. The converter should be rated at a level that is at least twice the rating of the motor on the equipment i.e. a 5hp guillotine requires a 10hp rated rotary converter.
Static converters - Maximum single motor load?
The starting characteristics of a three-phase motor supplied by a static TRANSWAVE converter are generally similar in nature to that of a star/delta starter. The motor starting current is suppressed by the converter to approximately 3 times the full load current of the motor, significantly reducing the amount of available starting torque. This leads to starting difficulties, particularly if the maximum loading of the converter is sized close to the load of the motor. The maximum single motor rating reflects the largest single motor the converter is capable of starting. The maximum loading of the converter reflects the maximum multi-motor running capability. Where possible, the use of direct-on-line starters is recommended for machinery operated in conjunction with a TRANSWAVE converter - note that the combination of a converter and a star/delta starter could compound these starting difficulties further.
Static converters - Minimum load?
Motors driving a table rise/fall, scribing saw, feed rollers, coolant pump or table feed are invariably of a fractional horsepower nature. If operated independently from a TRANSWAVE static converter, these motors would be subjected to an electrical condition, which would damage the motor windings. The minimum load reflects the minimum size of motor capable of interfacing independently with the converter, thereby establishing an acceptable artificial three-phase supply. Ancillary motors sized below the minimum loading of the TRANSWAVE should be operated in conjunction with and not independently of a larger drive motor that falls within the rating of the converter. Note that the Rotary converter does not have a minimum load.
Starting Currents/Star-Delta Starters
The full load running current (flc) of an induction motor operating on a single-phase supply is approximately 4 amps per hp. When operated in conjunction with a TRANSWAVE Converter, the starting current of a three-phase motor is limited to approximately 3 times its flc. This is significantly lower than the motor starting current of an equivalent sized single-phase motor, which would typically draw between 6-8 times its flc.
As the starting characteristics of a three-phase motor supplied by a converter are similar in nature to Star/Delta starting on a three-phase supply, significant reductions in starting torque are experienced when compared with direct online starting on a three-phase supply. Generally, when machinery is operated in conjunction with a TRANSWAVE Converter direct online starting is recommend. For machinery fitted with a Star/Delta starter, the period in the star connection should be set as short as possible to ensure a successful start. We may invite you to alter the Star/Delta timer setting to facilitate the above. This is not the case when machinery is operated on a mains three-phase supply.
Variable Speed Drives (often referred to as Inverters or Frequency Converters)
PCL is a Tier One Reseller of IMO
Inverter Products. All inverters are offered with a 2-year
manufacturer’s warranty. Please ask for details.
Both “3-wire” 415v three-phase and “2-wire” single-phase 415-volt welding sets can be operated with a suitably rated rotary converter. As welding load is resistive, not inductive, it is necessary to use a rotary converter to develop the voltage in the “artificial” third phase, independently of the welder. The converter should be of sufficient capacity to maintain the voltage on the artificial phase when the welder is operated at its maximum current rating. Some converter sizes need to be modified for welding purposes. This modification incorporates a hand/auto switch, which bypasses the automatic boost circuit. Two-phase welding sets can also be operated from dedicated transformers. Note that any rotary converter used for welding purposes can still be used for standard motor applications. Please seek advice from our sales staff